The current requirement for equipment is to be safe and efficient, especially for the most important boiler in production. The boiler will deposit scale after being used for a long time, which may cause uneven heating. The explosion-proof automatic water softening equipment eliminates electrical system failures and power failures and simplifies installation. This article will introduce the main points of its installation.
Nowadays, the technological level of equipment is getting higher and higher, and there are also general requirements for explosion-proof automatic water softening equipment. The equipment should be installed on a fixed platform and there should be sewers nearby, and the ambient temperature should be 2℃-50℃. The salt tank in the equipment should be placed close to the resin tank, and there should be space for operation and maintenance near the equipment.
Explosion-proof automatic water softening equipment has advanced technology and high overall requirements. Especially when the equipment controller is installed and the resin is filled, the lifting pipe should be put into the center of the resin tank 0.5mm below the tank mouth to cut off and lead the angle before filling. After installing the water distributor, turn the control valve clockwise until the control valve is screwed on the tank interface.
We all know that equipment includes many systems, and the cooperation between them can ensure efficiency. Explosion-proof automatic water softening equipment pipeline connection, according to the controller caliber connect the inlet and outlet water pipes. In order to facilitate the inlet and outlet water pipes, manual valves should be installed, and no valves should be installed in the drainage pipes. The distance between the control valve of the drainage pipe and the drainage ditch should not exceed 6 meters.
From the above, it can be seen that in order to prevent the equipment from malfunctioning during operation, many installation points must be paid attention to. When installing the explosion-proof automatic water softening equipment, it should be noted that the electrical connection power socket should have an independent switch. Do not open the water inlet valve quickly during the trial operation of the equipment, and open the water inlet valve after the air is drained.