Raw water source: municipal water, tap water, well water
Raw water TDS: 2000ppm
Pre-treatment: sand filter, activated carbon filter and softener.
RO unit: sediment filter, high pressure pump, RO membrane, pressure gauge, flow meter and pipelines.
Permeate output quality：TDS≤60-100 ppm, WHO direct drinking standard.
Salt rejection: 99%
Recovery rate: 50%
Frame material: stainless steel
Power supply: 380V/220V/110V,50/60Hz, 3.0KW
Certificate: CE certificate, ISO9001
1. Brief introduction of S2T-6000GPD RO Water Treatment Plant
S2T-6000GPD Water Treatment Plant is pure water ro plant treatment system 99% high salt rejection water purifier. It’s high recovery reverse osmosis water treatment system 1000LPH RO. The product pure water could be used for commercial, industrial, filling factory or for drinking of schools, hotel and home. The feed water TDS is 2000ppm, and product water TDS could below 100ppm and meet requirement of WHO drinking water standard.
The device is integrated structural design. The hoses and threads are properly sealed. Its small volume is for easy movement, installation and maintenance. The materials for the device are corrosion-resistant, reinforced plastics, nickel-aluminium bronze, to solve the water corrosion problem.
The S2T series are RO unit used for treating water with TDS below 2000ppm, such as tap water and municipal water. This series are standard designing and installation, which include water pump, membrane, sediment filter, etc. The permeated water after treated can drink directly. S2T series have been exported to many countries, such as Bahrain, Middle east and East Asia.
2.Technical route and flow diagram instructions
The technical route is as following.
Raw tank–> sand filter–> carbon filter–> softener –> sediment filter–>high pressure pump–>RO desalination device–>permeate tank
3. Specification for RO Water Treatment Plant:
|Model||Capacity (LPH)||3rd year operating pressure(PSI)||No. Of 4”element||4″membrane vessel||Designed recovery||Driving motor 50Hz/380V|
4. Weights & dimensions for RO Water Treatment Plant
|Model||Approximate unit dimension||Approximate shipping dimension|
5. Components of RO Water Treatment Plant
- T.F.C.R.O membrane with 99% average salt rejection
- FRP pressure vessel
- SS centrifugal pump
- Coated carbon steel frame
- Sediment filter
- Product water flow meter
- Concentrate regulate valve
- Pressure gauge
- Pump exit regulate valve
- 380V/50HZ power supply
- 304SS pressure vessel
- CIP system
- Concentrate recycle
- Chemical dosing system
- 220V/60HZ power supply
6. Our Certification
7. Comments From Customers
8. Package and Transportation