1. Brief introduction of Iron remove filter system
Iron remove filter device is to remove iron in raw water. Iron in ferrous state (Fe2+) is soluble, if it is oxidized to its ferric state (Fe3+), it is insoluble and can foul RO membrane. Beside that, high iron concentration in raw water can rust pump, piping and other iron components.
The majority of the water extracted from the deep wells will carry iron, mud, particulate matter, odor, can not be used directly, we do a good understanding of the well water in rural areas, the fundamental solution to the problem of the smell of water, the use of well water filter provide to family a healthy environment.
The filter is assembled by FRP tanks or carbon steel tanks, multi port filter control valve, distributor and filling material. Backwash modes could be manual multi port valve or automatic pre-set multi port valve or PLC control.
2. Specification of Iron remove filter system
|iron remove filter device||Φ500×1900mm，Q=5m3/h||SET||1||glassfiber reinforced plastics|
|upper and bottom water distributors||H182、HU6370A||SET||1|
|quartz sand filter||0.5-1.2mm||kg||150||0.4m|
|landing pressure gauge||0~1.0MPa||PC||1||stainless steel|
3. Projects information for Iron remove filter system
|Introduction of project|
|User introduction||Beximco Pharmaceuticals Ltd (Beximco Pharma) is an emerging generic drug player committed to providing access to affordable medicines. Company’s state-of-the-art manufacturing facilities have been accredited by the regulatory authorities of Australia, European Union, Canada, and Brazil, among others, and it currently focuses on building presence in many emerging and developed markets around the world.|
|Beximco Pharmaceuticals ltd build new factory in 2016, and they need potable water for drinking and softening water for their production.|
|Feed water quality||The feed water is from well, and the hardness is 170ppm, TSS is 40ppm,and iron is 1.5ppm|
|Capacity:||73.5m3/hr capacity pre-treatment systems for potable water and 27.5m3/hr capacity soft water ssytem|
|Output water quality:||Hardness<170ppm, TSS <1ppm,and iron is 0.01ppm|
5. Comments from customers:
6. Package and transportation:
7. Finished projects: