The raw water: Lake water
Flow in water TDS: N/M
Production: 20 m³/h
Recovery rater: ≧90%
SS in UF production water: ≦1ppm
UF membrane: SVU-1060-C
Material for UF membrane:mPS
Quantities for UF membrane:20 pcs
Manufacturer of UF membrane: Canpure
The raw water: Lake water
1. Brief introduction of Industrial UF purification equipment
Industrial UF purification equipment at capacity of 20TPH for water with suspended solids and bacteria and virus. With a high rate of bacteria and filtration.
It is a purification, separation or concentration of semipermeable membrane in separation techniques for solution. After more than 20 years rapid development, it has become one of the widest techniques in separation field. It widely uses in food and beverage, chemical electron, biological construction for environmental protection, etc.
Ultra filtration membrane is used to remove suspended solids, colloids, microorganism, bacteria,virus and macro molecule organism from the raw water.It has good function of color removing, oil removing, turbidity removing, COD and BOD removing. UF technology can be adopted under condition of normal temperature and low pressure with low energy consumption
This system use Canpure outside-in ultrafiltration membrane modules, the material for the membrane is PVDF, it can cleaned thoroughly by strong oxidant and is good at chemical resistance, mechanical strength and longer life time. This UF system is designed to treat well water with high suspended solids, microorganism, bacteria and virus. Each UF membrane have very good function to remove it. Ans the output water is for washing water supply.
2. Application of Industrial UF purification equipment
2.1 Pure and ultrapure water equipment,
2.2 No bacterium no heat raw water equipment for pharmacy,
2.3 Purification for beverage, drinking water and mineral water,
2.4 Separation, concentration and purification in industry
2.5 Wastewater treatment, electrophoretic coating, electroplating, oil wastewater treatment, etc.
3. Features of Industrial UF purification equipment
3.1 High precision. The bore diameter of UF membrane is 0.001~0.1m. Which can remove bacteria, colloids, rust and macromolecule organism effectively and ensure the output water quality stable with less COD,SS and SDI.
3.2 Pro-long RO membrane cleaning peroid and life time by adopting UF as pre-treatment
3.3 With universal wheels so easy to move.
3.4 Compact frame with less space.
3.5 Low work pressure, low operation cost.
3.6 Easy and safe operation.
3.7 Easy maintaining.
4. Main parts and specification
|4.1 Multi media filter||two sets|
|Material of filter cartridge:||light FRP tank|
|4.2 Sediment filter||one set|
|Sediment filter cartridge:||20pcs|
|Model:||2.75×40” ×50 um|
|4.3 UF filter||one set|
|Bacteria rejection rate:||≥99%|
|Designed recovery rate:||90%|
|Suspended matter, particulate( >0.2μm):||100% rejection rate.|
|Max feed water pressure:||0.4Mpa|
|Backwashing water flow meter:||WLG-8350,1pc|
|Flowing water flow meter:||WLG-8350,1pc|
|Outlet water flow meter:||WLG-8350,1pc|
|Cross-flow r flow meter:||WLG-8350,1pc|
|System valve:||water motorized valve, washing water draining motorized valve, UF producing water motorized valve,Up-draining motorized valve, Down-draining motorized valve, Back washing water motorized valve|
5. Working condition
|Max. feed water pressure:||0.4Mpa|
|Max. pressure difference of membrane:||0.2Mpa|
6. Performance table of Industrial UF purification equipment
|Pre-treatment||50-150um precision filter|
|Max. feed turbidity||≤15NTU||When feed water turbidity is more than 15NTU，please add pre-treatment and precision filter.|
|Running method||Cross flow/dead end flow||Dead end flow can be adopted when feed water turbidity less than5NTU. Otherwise, cross flow type is suggested.|
|Feed water pressure||0.1~0.3MPa|
|Max. feed pressure||0.5Mpa|
|20℃ transmembrane pressure（TMP）||28-150Kpa|
|Max. transmembrane pressure||0.2Mpa|
|Max. residual chlorine||100ppm|
7. Specification for membrane
|fiber inlet/outlet diameter||0.9mm/1.5mm|
|Detained molecular weight||100，000dalton|
|Effective membrane surface||28 m²|
|Membrane housing material||ABS|
|End cap material||Epoxy resin|
|Max.feed water pressure||0.5MPa|
|Max.membrane pressure difference||0.2MPa|
|Feed water PH||2-12|
|Permeate turbidity||< 0.1NTU|
|Silt density index（SDI）||< 1|
|Suspended solid，particle（>0.2µm）||100% removed|
|Feed water quality requirement||turbidity≤15NTU. （pretreatment should be added when the raw water is from ground, river and well. It is recommended to add precision filter, 100um at least in precision, to ensure the turbidity no more than 15NTU）|
8.Technical route for Industrial UF purification equipment
Raw water was firstly pressurized by raw pump and then filled into sediment filter to remove the substances over 5um. Then feed into ultra filtration system for treatment, concentrate water was discharged or recovered, the permeate water feed into the UF tank. After operation for a while, the equipment should be chemical cleaned. Refer to the Appendix.