The raw water: Lake water
Flow in water TDS: N/M
Production: 2000 L/H
Recovery rater: ≧90%
SS in UF production water: ≦1ppm
UF membrane: SVU-1060-C
Material for UF membrane:mPS
Quantities for UF membrane:20 pcs
Manufacturer of UF membrane: Canpure
The raw water: Lake water
1. Brief introduction of Ultra filtration system 2000LPH
UF water treatment plant for pre-treatment of RO, adopted ultra filtration system 2000LPH with high quality. It mainly used for irrigation, industrial or commercial water purification plant.
Ultra filtration membrane is used to remove suspended solids, colloids, microorganism, bacteria,virus and macro molecule organism from the raw water.It has good function of color removing, oil removing, turbidity removing, COD and BOD removing. UF technology can be adopted under condition of normal temperature and low pressure with low energy consumption.
2. Features for Ultra filtration system 2000LPH
2.1 High precision. The bore diameter of UF membrane is 0.001~0.1m. Which can remove bacteria, colloids, rust and macromolecule organism effectively and ensure the output water quality stable with less COD,SS and SDI.
2.2 Pro-long RO membrane cleaning peroid and life time by adopting UF as pre-treatment
2.3 With universal wheels so easy to move.
2.4 Compact frame with less space.
2.5 Low work pressure, low operation cost.
2.6 Easy and safe operation.
2.7 Easy maintaining.
3. Parameter table
|Pre-treatment||50-150um precision filter|
|Max. feed turbidity||≤15NTU||When feed water turbidity is more than 15NTU，please add pre-treatment and precision filter.|
|Running method||Cross flow/dead end flow||Dead end flow can be adopted when feed water turbidity less than5NTU. Otherwise, cross flow type is suggested.|
|Feed water pressure||0.1~0.3MPa|
|Max. feed pressure||0.5Mpa|
|20℃ transmembrane pressure（TMP）||28-150Kpa|
|Max. transmembrane pressure||0.2Mpa|
|Max. residual chlorine||100ppm|
4. Specification for membrane
|fiber inlet/outlet diameter||0.9mm/1.5mm|
|Detained molecular weight||100，000dalton|
|Effective membrane surface||28 m²|
|Membrane housing material||ABS|
|End cap material||Epoxy resin|
|Max.feed water pressure||0.5MPa|
|Max.membrane pressure difference||0.2MPa|
|Feed water PH||2-12|
|Permeate turbidity||< 0.1NTU|
|Silt density index（SDI）||< 1|
|Suspended solid，particle（>0.2µm）||100% removed|
|Feed water quality requirement||turbidity≤15NTU. （pretreatment should be added when the raw water is from ground, river and well. It is recommended to add precision filter, 100um at least in precision, to ensure the turbidity no more than 15NTU）|
5. Output capacity for different application:
|Raw water source||Max.output capacity(m³/h)||Min.output capacity(m³/h)|
|Superficial layer under ground water||3.1||2|
|Deep layer under ground water||2.2||1.8|
|City recycled water||2.3||1.8|
6.Technical route for Ultra filtration system 2000LPH
7. Certificate of Ultra filtration system 2000LPH
8. Comments from customers:
9. Package and transportation:
10. Finished projects: