Product name:RO membrane
Effective membrane area:34m²
PH range for continue working:2-11
PH range for cleanig:1-13
Applicable Industries:Hotels, Manufacturing Plant, Food & Beverage Factory, Farms, Restaurant, Home Use, Food & Beverage Shops
After Warranty Service:Video technical support, Online support, Spare parts, Field maintenance and repair service
Filmtec RO membrane bw30-365
Product name:RO membrane
1. Brief introduction of Filmtec RO membrane bw30365
Filmtec RO membrane bw30-365 is good quality for water purification. RO membrane bw30365 is useful for water desalination plant. The membrane area is 34m² and with capacity of 9500GPD, salt rejection of 99.5%.
BW30-365 element is the product of choice when the highest quality permeate is required. It was the first 365 square foot membrane elements on the market and continues to be widely used in new equipment and retrofits where system capital and productivity are factors.
Filmtec superior automated manufacturing technology results in the most consistent performance element-to-element and year-after-year.
BW30-365 elements deliver high flow and high rejection without being chlorinated during the manufacturing process. This is one reason why FILMTEC elements are more durable and may be cleaned over a wider pH range (pH 1 – 13) than other RO elements.
*With more than a decade of proven performance, BW30-365 is the product you can rely on for years of trouble-free operation.
2. Parameter and test condition for Filmtec RO membrane bw30365
|Product Name||Nominal Active Surface Area ft² (m²)||Permeate Flow Rate gpd (m³/d)||Stabilized Salt Rejection(%)||Minimum Salt Rejection(%)|
|FILMTEC BW30-365||365 (34)||9,500 (36)||99.5||99.0|
2.1. Permeate flow and salt rejection based on the following test conditions: 2000 ppm NaCl, 225 psi (15.5 bar), 77°F (25°C), pH 8, and 15% recovery.
2.2. Flow rates for individual elements may vary but will be no more than 15% below the value shown.
2.3. Sales specifications may vary as design revisions take place.
2.4. Active area guaranteed +/-3%. Active area as stated by FilmTec is not comparable to nominal membrane area often stated by some manufacturers.
3. RO membrane principal and related drawings
Permeate flow rate and salt rejection based on the following test conditions: 2000 ppm NaCl, 225 psig (15.5 bar), 77°F (25°C), and 15% recovery. Permeate flow rates for individual elements may vary +/-20%. For the purpose of improvement, specifications may be updated periodically.
4. Package for Filmtec RO membrane bw30-365