Power: 14w, 14w
Packing Material: carton
Applicable Industries: Hotels, Manufacturing Plant, Food & Beverage Factory, Farms, Restaurant, Home Use, Retail, Food Shop, Food & Beverage Shops
Flow rate: 2gpm
Water capacity: 500LPH
Chamber: stainless steel
Lamp life: 9000hours
Electrical power: 220V/50HZ
Inlet/Outlet: 1/4″ BSP
Application: pure water, pool
Pool uv sterilizer 2gpm
Power: 14w, 14w
1. Brief introduction of Pool uv sterilizer 2gpm
UV sterilizer 2GPM for pure water 500LPH sterilization ultraviolet light sterilization equipment for pool water swimming water disinfection. The lamp is 9000 hours. It is also widely used in water treatment. After RO treatment, the permeate water goes through the UV for disinfection and the water will be safe to drinking.
|Model||Water flow rate||inlet/outlet||lamp model||Power|
3. Application for UV Sterilizer water purifying
- Drinking water disinfection,tap water,pure water
- Food and beverage water,industrial process water
- Swimming pool and spa,scenery water,irrigation water
- Waster water disinfection
- Cooling tower and Ro system
4. Dimension for UV Sterilizer water purifying
5. Assembly parts drawing
6. Maintenance suggestion UV Sterilizer water purifying:
To operate the sterilizer properly and attain its maximum efficiency that the user need to do some maintenance jobs as below:
Quartz sleeve cleaning or replacement
- Quartz sleeve is to be cleaned every 3~6 months, clean with alcohol or detergent.
- Quartz sleeve is to be replaced every 24 months.
UV lamp replacement is recommended every 8000~9000 hours of operation (approximately 12 months of continuous service)
- Remove water proof strainer 1 and unscrew the nut 2.
- Carefully withdraw lamp 4 approximately two inches from chamber7
- While holding lam end 4 carefully remove lamp socket 3 on end now exposed.
- Carefully withdraw lamp 4 from chamber7
- Carefully remove O-ring5 from both end of quartz sleeve6
- Carefully remove quartz sleeve