Feed water source: Borehole Water, Salt Water, Underground Water, Well Water.
Feed Water TDS: 9000ppm
Pre-treatment: Carbon Filter, Sand Filter, Water Softener
RO unit: Sediment filter, High pressure pump, RO membrane, Pressure gauge, Flow meter and Pipelines.
No. of 4″ RO membrane: 5pc
Permeate output quality：TDS≤60-100 ppm, WHO direct drinking standard.
Salt rejection: 99%
Recovery rate: 30%
Frame material: stainless steel
Power supply: 380V/220V/110V,50/60Hz, 5.5KW
Certificate: CE certificate, ISO9001
1. Brief introduction of Brine Water Fresh Treatment
Brine water treatment make the high salt water with TDS of 12000mg/L to fresh drinking water. Food & Beverage Factory Applicable Industries brand new 1500LPH brackish water treatment reverse osmosis water system price from CHIWATEC B2K series.
B2K9 series are used to treat brackish water with TDS from 9000 to 12000ppm. The system adopted the world’s most advanced reverse osmosis technology. Different models are designed as per different feed water salt content and capacity. The quality of output water meets the WHO drinking water standard.
2. Features for Brine Water Fresh Treatment
►Use DOW FILMETEC design software to calculate and simulate, providing the theory guideline for design.
►We design different systems according to feed water quality and required capacity, the B2K series are applicable to the raw water with salt content 9000ppm-12000ppm. If salt content is above 15000ppm pls choose SW series for seawater.
►Water quality(TDS) monitor device to ensure stable output quality.
►High salt rejection, service life longer than 3 years, low operation and maintenance cost.
►PLC automatic control.
►Unique fresh water automatic replacement device to replace concentrate in the membrane with fresh water when system stops to reduce membrane pollution, therefore prolong the service life and lower cost.
►Carbon steel coated and stainless steel frame for choice, moving wheels can be installed for different installation situation.
►Stainless steel and SCH80UPVC pipelines with high quality to ensure no leakage and low corrosion under high pressure.
Daily drinking water for buildings, hotel rooms, factories, schools, etc.
For mobile working organizations such as ocean voyages, drilling units, field exploration, tec.
Desalination of water used in production techniques.
4.Technical route and flow diagram instructions
The technical route is as following.
Raw tank–> sand filter–> carbon filter–> anti-scalant dosing system –> sediment filter–>high pressure pump–>RO desalination device–>CIP system–> permeate tank
5. Specification of Brine Water Fresh Treatment
|Designed recovery||No. Of 8” element||Membrane vessel spec.||Operating pressure(bar)||Driving motor(kw)|
6. Operation parameter for Brine Water Fresh Treatment:
|Water source||Underground water|
|Raw water TDS||<12000mg/l|
|Designed salt rejection||99.60%|
|Designed recovery rate||33%|
|Product water TDS||241mg/l|
|Raw water pump||CHL8-40|
|Pre-treatment||Multi-media filter+anti-scalant dosing system|
|High pressure pump||CRN5-36|
|Pressure vessel||Spec.||4080A-450PSI, FRP|
|Main frame size (mm)||2100×800×1500|
|Power supply||380v,50hz,triphase(220/110v, 60hz, single phase for option)|
8. Comments from customers:
9. Package and transportation: